write integer with command Forum Home › Forums › Communicating with Devices › write integer with command This topic contains 1 reply, has 2 voices, and was last updated by Mikhail 1 year, 2 months ago. Viewing 2 posts - 1 through 2 (of 2 total) Author Posts May 10, 2018 at 4:49 pm #3706 Charles CoolParticipant I have been trying to modify a register in a PLC from RAPID SCADA. I can read the register with a dynamic text but when I click on it I do not get anything to input a number to modify the register. Could you explain the procedure to set this up? May 11, 2018 at 4:38 pm #3707 MikhailModerator Hi, You should: 1. Create an output channel in the configuration database. 2. Specify the number of the output channel for a scheme component. And set the Action property of the component. 3. Create a command in your Modbus template. Author Posts Viewing 2 posts - 1 through 2 (of 2 total) You must be logged in to reply to this topic.