April 22, 2016 at 10:10 am #1005
Scada Web is working fine on my own computer but, when i try to open it on another computer it does nothing. Stay forever loading but don’t open and them after a very long time it says:
This site can’t be reached
192.168.0.12 refuse to connect
192.168.0.12 is my computer IP (where RapidScada is installed), Windows 8.1.
Do i need to install something on or the other computer as well? How about for android phone?
Did i forgot to install something in my computer, or did i install too much?April 22, 2016 at 10:14 am #1006
First of all, make sure that the web site on 192.168.0.12 is accessible: try to open http://192.168.0.12
If not, may be the cause is firewall.January 29, 2017 at 8:36 am #1907
The access from any computer within the home-network to the SCADA server works perfect, but how can I access the server from the internet? I’ve opened a port 10000 on the router/modem, and on the SCADA server (a new rule in the firewall). I have a static address (via dyndns). Then I tried with:
but it didn’t work. Is it enough just to open the port? Which application should I start behind this port.
January 29, 2017 at 10:54 am #1909
- This reply was modified 1 year, 11 months ago by tom040264.
Does your web server located within home network or on a hosting in the Internet?
Seems you perform the right settings. What errors in log files of server and web application?January 29, 2017 at 10:55 am #1910
Also you can install this utility and try to establish a connection between internal and external computers.January 29, 2017 at 12:05 pm #1911
It seems as if it is a small misunderstanding. I understood, that Rapid SCADA has an integrated WEB-server, and the other computers hold the data from it.
I have no web server, neither i my home network, nor in the internet.January 30, 2017 at 9:29 am #1912
Could you provide more details about the architecture of your system?February 1, 2017 at 9:34 pm #1920
The architecture is easy: a Win10 computer 24/7 as SCADA server, some Win10 or android clients. From each of them I can reach the server, but from the internet it is not possible. The router/ modem is a FritzBox 3390.February 2, 2017 at 6:46 am #1922
You need to open port on Windows Firewall, allow incoming connection on the router and redirect data to your PC using NAT (on router).
There is no SCADA specific, just network administration.February 2, 2017 at 6:51 am #1923June 14, 2018 at 12:21 pm #3834
It is a very old tread, but unfortunately I am still not able to connect to SCADA from “outside” of my Network. In the meantime it is not possible to open the Image you posted a year ago.
What did I do? I opened a port 10000 on my router (Frizbox 3390) and rerouted it to the posrt 10000 on my SCADA Computer. On this computer I opened in firewall a port with the number 10000. Is this the right way?
Thx in advance
T.June 14, 2018 at 6:51 pm #3835
Seems, you do the right things.
Can you open Rapid SCADA from other computers within your network?
How do you connect from the outsite? Do you use dynamic DNS?June 15, 2018 at 2:32 pm #3838
I have found the error. It was in my modem-router. The port 10000 was open, and redirected, but (I am an idiot!) the standard WebPort 80 has not been opened.
Thank you and sorry for this misunderstanding.June 15, 2018 at 4:37 pm #3842
OK, thanks for the status.
You must be logged in to reply to this topic.