IEEE 754 floating point ?? Forum Home › Forums › Communicating with Devices › Modbus › IEEE 754 floating point ?? Tagged: IEEE 754 floating point This topic contains 3 replies, has 3 voices, and was last updated by rocks 2 years, 3 months ago. Viewing 4 posts - 1 through 4 (of 4 total) Author Posts July 22, 2017 at 1:13 am #2384 rocksParticipant Dear Sir, I find this software very useful, I think we can use it for implementation , but I need to test it properly its stability and usefulness. Please let me know if it can read and process the energy perameter present in IEEE 754 floating point 32 bit modbus signal. July 22, 2017 at 7:07 am #2385 manjey73Participant Connecting Devices Using Modbus Protocol Element parametrs float(4 bytes) Byte orders, you must specify your sequence of bytes, for example 2301 In the initial group element specifies the starting register in the survey. Depending on the equipment it may be necessary to the starting address add 1 July 23, 2017 at 7:00 am #2386 MikhailModerator Hi Rocks, Its better to specify your questions in details providing screenshots and logs August 11, 2017 at 2:01 pm #2478 rocksParticipant Sir, It is responsing with 2301 order thanx. Author Posts Viewing 4 posts - 1 through 4 (of 4 total) You must be logged in to reply to this topic.