Now i return to my idea: to send a command to relay board from Communicator via TCP/IP using RS485-Ethernet converter. Can the communicator do it? If it can so how to configure?
Thanks a lot
The Ethernet-RS485 Converter has an IP and port and a TCP server management mode. In the Line settings, you need to configure as a TCP client by specifying the IP and port. Leave the Modbus RTU setting.
Dear manjey, every thing is good. I am able to control relay remotely via TCP. It is great.
Now i am going to configure a rapid scada to send commands from buton in the scheme. Can it? How to configure it?
Thanks a lot.
It will be difficult for me to explain to you, since I use the latest version of RapidScada in Russian
You need to create input and output channels for your device.
Create an interface with a button.
In the properties of the button, specify the input and output channels.
Option 1. In the output channel, specify “Use formula”, specify the value 768. This way the button will always send a trigger command to the relay
Just specify in the properties of the button-send the command immediately.
To create two buttons with different purpose-Enable or disable. It will be necessary to make a duplicate of the output channels, in one of them as a formula to specify 256 (Disable), in the other 512 (Enable). Or use a more complex formula in one output channel
After Lunar New Year holidays i was tried to configure rapid scada to send commands to Relay board via scheme but i have not get the result. Could you help me how to create output channel? You can explain it by Russian. I can read it.
Thanks a lot