Tagged: raspberry pi
September 12, 2015 at 3:32 am #448
I should clarify the info I sent you was from a third party software looking at the signals recived by com port the problem I am haveing is the modbus first register is not the one I typed in if I change it the out put allso changes however it is all over the place the no of registers is allso wrong however all other relevent data is correct eg the device Id and function code as for the log ill attach it bellow.
AsaSeptember 12, 2015 at 7:06 pm #451
Please look the file /etc/scada/ScadaComm/Log/lineXXX.log
(where XXX – your communication line number)
for the addition informationSeptember 12, 2015 at 9:55 pm #455
The only error in the log is as follows it is listed multiple times
Date and time communication session with device 100 “A/W PLC”, type kpmodbus address 100 call number 100
Request element group
Send (8): 64 04 00 0A 00 16 58 33
Receive (0/5) :
Now the device was not attached however it would not work anyway with those registers as they are unused.
Hope this helps
AsaSeptember 13, 2015 at 6:13 am #456
Ok with the info above I have adjusted the .xml file address to 10 to see if there was a change in the signals received there was
The program log states it sent : 64 04 00 0A 00 16 58 33
That is correct however
In reality it sent :64 04 80 85 80 8b AC E6
AsaSeptember 13, 2015 at 7:46 am #458
Seems that problems are in the USB adapter or the wires. If you connect this adapter to Windows computer, does it work correctly?September 13, 2015 at 7:48 am #459
Yes it works correctly on windows i have tested the whole system on windows and it works.
AsaSeptember 13, 2015 at 8:05 am #460
What I don’t get is how some of the command is correct but the rest is all wrong.September 13, 2015 at 12:34 pm #468
It seems like problems in the equipment.September 15, 2015 at 7:52 am #474
Is it possible to use Rapid Scada with Windows 10 IoT on Raspi? I guess running Scada Web could be a problem (not sure whether there is IIS for Windows 10 IoT), but having just Communicator and Server working would also be quite nice.
DejanSeptember 15, 2015 at 8:14 am #475
I’m sure, it is possible, but hasn’t be done before. If you’d like to do it, I’ll try to help you.September 15, 2015 at 11:02 am #480
Thanks Mikhail, I’ll try it when I have some time.
DejanNovember 3, 2015 at 2:10 pm #643
Can rapid scada be installed in Windows 10 IoT core on Raspberry pi 2?? Will it support scada web component?? Need info to select for my project.November 4, 2015 at 3:31 pm #645
Most likely SCADA-Server and SCADA-Communicator can be installed on Windows 10 IoT on Raspberry, but I have no information about such experience. I think that SCADA-Web requires some modifications to work on Win 10 IoT. If you decide to try it, I’ll help you.
At the moment Rapid SCADA is tested on Raspbian.November 5, 2015 at 4:37 am #649
Thanks for reply. Is it tested for full functionality on raspbian ??November 5, 2015 at 8:41 am #652
As a restriction: scheme views do not work for now, table views and charts are OK. This issue will be taken into account in the future version of SCADA-Web.
Classic OPC of cource does not work on Raspbian bacause it is based on DCOM.
You must be logged in to reply to this topic.