Forum Replies Created
Thank you, i did activate it. In security i give modify permission to User account.
Remote software is not turn on 100% of time. We use software only to check is device working properly. The problem with connection occurs when remote software wasn’t active at all. There must be something else that result problem.
i want to apologize for late response but i talked with my boss and he will contact you about details for method 1.
I will contact my boss but i think we will be more interested into method 1.
I tried with accounts: ScadaWeb,ScadaComm,ScadaServerCtrl and ScadaAdmin and still wasn’t able to download configuration. I also watched to input appropriate password for each account.
I view user.dat and i see there ScadaAdmin with password 12345 and roleID=4, after that i check roleID settings and 4 is application role.
I added user ScadaAdmin with password 12345 and application role. Pass that to server. I didn’t do migration yet. I wanted to download configuration from old version (5.6) and error occur with login.
Also i wonder about system instance = default. Maybe i need to change that?
I wanted to fix this before i try migration from 5.6 to 5.7. Thank you for that file about migration.
2019-08-27 18:47:36 <computer_name><SYSTEM><ACT> Session with ID 3350479412239322651 created
2019-08-27 18:47:36 <computer_name><SYSTEM><ERR> User ScadaAdmin failed validation to connect to Default – Invalid username or password
2019-08-27 19:01:40 <computer_name><SYSTEM><ACT> Session with ID -7675101413440856990 created
2019-08-27 19:01:40 <computer_name><SYSTEM><ERR> User ScadaAdmin failed validation to connect to Default – Invalid username or password
Thank you very much. It’s working now.
Can you be more specific? How should i setup input and output channel in that case?
Just to give you example what i want to do. I want to press some box that will open popup like you want to send command and there you have window where you input some value 25 or 53 or 86 and when you press ok and popup closed i want to see that value in some input channel.
I can’t store some value in variable.
I need to apologize because i found mistake in peripheral device(blocking value at 32727). That means communicator is working correctly.
Can you be more specific because like i said i check option for data to be ushort in Communicator?
This is working but i notice SCADA making event when status changed. From OFF to ON or ON to OFF.
What should we do if we want to make event only when status go from OFF to ON?
I want to use event trigger in automatic control module to send some email that give notification to user that something is in alarm status. In this case i want to send email when discrete channel is in true status and not send email when discrete channel go back to false status.
I found mistake. Forgot to put address 1 in device setup page in scada administrator.
Now is working correctly.