Forum Replies Created
This data only in the files in C:\SCADA\ScadaComm\Log
“Have You Tried Turning It Off And On Again?” 🙂
Thanks for noticing.
A device 192.168.0.103 rejects the connection. The problem is on its side.
Try to connect to the device using another application.
If something goes wrong, I always have a backup project.
That’s good. I suggest GIT to control changes in a project.
Please ask specific questions.
If a connection between a device and Communicator is broken, you will get empty values after next polling attempt.
If a connection between Communicator and Server fails, you will get empty values after a certain period of time.
Currently no. However, it can be implemented in the future. Thank you for the idea.
“Fit to Screen” also remembered.
1. Open the demo.
2. Open “Home scheme”
3. Click the Fit to Screen button.
4. Open “Server room scheme”
5. You will see that the last scheme is also fit to screen.
Please describe the expected behavior of the software to understand the question.
Try clearing browser cache. If it doesn’t help, please provide a link to a screenshot with the error.September 10, 2020 at 12:54 pm in reply to: How to install Chart Plugin and Elastic report modules on Raspberry Pi4 #7252
Installation is described here. If you use Linux, change directory C:\SCADA\ to /opt/scada/
You should update Rapid SCADA to version 5.8.1 to fix this issue.
This error caused by version mismatch.
You have the latest Chart Pro, but Webstation looks outdated.
Could you check the timestamp of C:\SCADA\ScadaWeb\bin\ScadaWebCommon.dll file?
We have a minor bug that after updating Webstation, it’s version number still 22.214.171.124. That’s why it’s better to check file age.
It’s better to edit a project on Windows and then upload it to Linux.
If you can only use Wine, please send C:\SCADA\ScadaAdmin\Log\ScadaAdmin.err May be it’s possible to fix.